Also known as leach fields or leach drain, septic drainage fields are a very important part of the septic system.
What is a septic drainage field?
Septic drainage fields, sometimes referred to septic drain fields or foul water soakaways, are subsurface wastewater treatment facilities which are used to remove contaminants and impurities from the effluent that emerges from a septic tank. It usually consists of an arrangement of trenches, which contain perforated pipes and gravel, sited beneath a soft landscaped area such as a lawn.
As well as the septic tank, the septic drain field and any other connecting pipework make up the septic system. The septic tank only performs around 45% of the treatment work, the rest of the work is performed by the drain field; which is why it is so important to make sure it is designed correctly prior to installation.
The guidelines for the design of drainage fields can be found in Building Regulations Part H.1
Key facts and rules
- Septic tanks can only discharge to the ground via a drainage field. Discharge to a watercourse is not permitted.
- Drainage fields can only be used where the soil conditions are suitable.
- Site tests are required to determine if the soil on site in suitable.
- Drainage fields must be a minimum of 10m from a watercourse, 50m from a water abstraction point and 15m from a building.
- Before you start work on any septic drain fields you must not be in an Environment Agency Groundwater Source Protection Zone. This is to protect abstracted drinking water.
"That's all well and good but how do you go about installing one?" Fear not we've got you covered here with an installation guide.
How to determine the size of your septic drain field?
The size is also dependant on how many occupants and bedrooms the property has.
Ground which drains too quickly which, in most cases is sandy soils, is not suitable either as the effluent could drain too quickly and still be contaminated.
Test method from Building Regulations part H
A 300mm square should be excavated to a depth of 300mm below the invert level of the effluent distribution pipe. Measurements vary where deep drains and deep excavations are necessary; please refer to the Building Regulations Part H2, 1.34.
- Fill the 300mm square section of the hole to a depth of at least 300mm with water and leave overnight to seep away.
- The next day, refill the test section with water to a depth of at least 300mm and record in seconds the time it takes for the water to seep away from 75% to 25%. The divide this time by 150; the answer you get gives you the average time in seconds it takes for the water to drop 1mm.
- The above test should be carried out at least 3 times with at least two trial holes and then the average figure for all tests should be taken. The tests should not be taken in any abnormal weather conditions.
Drainage field disposal should only be used when percolation test indicate average values of between 12 and 100. The minimum value assures the untreated effluent cannot percolate too rapidly into the groundwater and the higher value assures effective treatment is likely to take place.